Acrel ASJ Series Residual Current Relay can be combined with low-voltage circuit breakers or low-voltage contactors to form a combined residual current protective device. It is mainly suitable for TT or TN system distribution lines with AC 50Hz and rated voltage of 400V and below. Equipment and electrical fire accidents, and can also be used to provide indirect contact protection against personal electrical shock hazards.
|Type AC||Type A|
|input||Rated residual actioncurrent I△n||0.03、0.1、0.3、0.5(A)||0.03、0.05、0.1、0.3、0.5、1、3、5、10、30(A)|
|Non-driving time oflimitation △t||0.1、0.5(s)||0、0.06、0.1、0.2、0.3、0.5、0.8、1、4、10(s)|
|Rated residualnon-action current I△no||50%I△n||50%Ian|
|performancecharacteristics||simple sinusoidal alternating current||simple sinusoidal alternating current andpulsating direct current|
|output||output mode||one is the normal closing and the otheris for the transformation||one is the normal closing or opening, andthe other is for the transformation|
|contact capacity||5A 250VAC|
|reset mode||theon-the-spotoneand the long-distanceone,||the on-the-spot one, the long-distance oneand the automatic one|
|power supply||voltage range||AC110V、AC220V(permissibleerror±10%)||AC110V、AC220V、DC85-270Vpermissible error±10%)|
|power frequency withstand voltage||The effective value of alternating current between the power supply, input and output: 2kV/Imin|
|under thenormaloperation||temperature||operating temperature:-20℃～+55℃storage temperature:-30℃～+70℃|
|humidity||≤95%RH,with moisture condensation,and corrosive gas place|
|height above sea level||≤2000m|
|class of pollution||Grade three|
|installation category||Type III|
Acrel Residual Current Device Using 32-bit high-performance CPU, real-time sampling of three-phase AC current and three-phase AC voltage signals, and using the effective value calculation method to achieve high-precision measurement in a wide frequency range. Integrated with a variety of protection functions, the protection can be put in or out, alarmed or tripped with a simple selection; high precision, low power consumption, fast action, high return coefficient, no jitter, and can be used for voltage monitoring (voltage type: Such as relay protection of generators, transformers and transmission lines, etc.) or current monitoring (current type: such as in overload and short-circuit protection lines of motors, transformers and transmission lines), as overvoltage, undervoltage, overcurrent, Blocking action element or starting element for undercurrent, overfrequency, underfrequency protection.
Not recommended. By this plan, at the moment of starting the high-power and high-frequency equipment, the vector sum of the output current of three-phase four-wire measurement transformer is not zero (directly measured is 0), which can easily lead to malfunction and tripping.
For reconstruct projects, if the wire diameter of the line is less than 100mm, open-type residual current transformers can be used. It is not recommended to use open-type residual current transformers larger than this aperture, because the measurement accuracy of the large aperture sensor is poor.
Reason one may be wiring error; Another may be wrong product selection.
This phenomenon is that the breaker will trip-out after the protected power supply is cut off; the other is to protect the line when undergoing dual power switching.ASJ series residual current relay is the type that automatically recovers and resets when the auxiliary power fails. According above-mentioned conditions, the instrument can be selected as the type that does not automatically act when the power fails.